In no event shall Honeywell be liable for technical or editorial omissions or mistakes in this document, nor shall it be liable for any damages, direct or incidental, arising out of or related to the use of this document. Text changes to Appendix D were made, and the manual was reformatted. Enter 14 in the address Addr? This indicates that the X529 has power and that it is executing its software. Refer to the document Palm Door Switch Tester Utility. If the switch address field remains blank, the Palm tester did not see any door position message traffic. Execute Parameter 1, value 14 to reset the X529 using Steps A through D below. To view and edit these local e529 parameters, you must enter the local parameter mode on the e529.
Typical use could be monitoring a door switch, for example, if the X529 was physically located close to the door. Table of Contents Introduction………………………………………………………………………………………………… 4 Section 1 1. The e528 features a guest-friendly graphic interface with intuitive controls Figure 2. The last number of the reported switch message indicates the battery state in the S541. There is no indication on the e529. The screws thread into two small holes on the bottom of the e529 housing Figure 3.
. . Check for the low battery symbol on the e529 display. Hook the tabs at the top rear of the e528 housing into the matching depressions at the top of the mounting plate and rotate the bottom of the housing toward the wall until it snaps into place on the mounting plate. Enter a different value if the X529 address is different.
Entering X529 Service Mode Execute the following sequence on the e529 battery thermostat: 1. The connector is buttoned to fit in only one direction. The problem is that once you have gotten your nifty new product, the inncom thermostat installation manual e529 gets a brief glance, maybe a once over, but it often tends to get discarded or lost with the original packaging. Close the battery clamp and verify the latch is securely fastened. . Avoid objects directly in front of the Eye5 module. .
If the door server status remains blank for a few seconds and then changes to No Srv! Tap the Start button to start the test. Enter the X529 address in the Addr? Appendix B — Setting the Address of the X529 Controller via the e529 Thermostat Follow Procedures 1, 2, and 3 to set the address of the X529 controller. . . . A low-voltage mounting plate, mud ring, or low-voltage caddy may be used for mounting 24 volt applications.
Honeywell makes no representations or warranties with respect to this document. Books in pdf and other formats are very convenient to read. Language: English Category: Inncom Publish: February 22, 2019 Source:. Cards in the Snap Track. The raw messages being sent from the X529 frame sent and replied from the target device frame rcvd are displayed. .
The number of times a read message was sent from the X529 to the target device, the number of responses received, and the success percentage are also displayed. These steps may require modification if controlling different equipment, such as a single fan speed Heat Pump with 2nd stage heat or equipment not capable of heating or cooling. Download Inncom Thermostat Installation Manual pdf into your electronic tablet and read it anywhere you go. Instead, the buttons and display on the e529 are used to view and change the X529 service parameters. Our links are always in a working condition.
Note: If two dots appear on the e529 display, that is okay. The X529 does not have its own display and buttons to view or change service parameter values. . The format of the captured data is shown in the example below. . .
. Using the search function you can easily find the books you need. A user guide for the e528, written primarily for installers and facility management personnel, is available see References below. If attaching the mounting plate to a sheetrock or similar wall surface, install four 6-8 X ¾ anchors. Let the trace continue to run for 30 seconds to make sure you got it all, then tap the Trc button to stop the trace. Mount the e529 Battery Powered Thermostat as follows: 1.
Quit the Device Configuration program on the Palm, and verify the trace text file was created on the Palm by doing the following steps. If the last number is 0, the batteries are good. Typical use could be monitoring a door switch; for example, if the X529 were physically located close to the door. Start the X529 Device Ping program if not already started. Increase the value to 14. If the last number is 1, the batteries are low and should be changed.